GMC has been a safe company for Miramar, FL to turn to for any air conditioning need since 2007.
With more than 30 years of experience, we know what it takes to be leading air conditioning providers in Miramar, FL. Read more in our reviews below.
for Miramar, FL
Our Reviews by City
Moriamo - Miramar, FL
We have been using their services for years now. Good and honest workers. Curtis did our recent AC check up, he was punctual, professional and knowledgeable about our unit. Thank you.
Response from GMC Air Conditioning Services, LLC:
Ms. Okegbenro, thank you for your business and thank you for sharing your amazing experience with our Technician Cirtis! We are delighted to hear of your great experience and we appreciate you sharing it!
Geoff - Miramar, FL
Johnny came out yesterday. Called first. On time. Very polite and respectful. Explained everything thoroughly. Had to come back today. Again on time and fixed everything. Ran into a small problem and fixed that as well. Will definitely request Johnny again for any AC needs. As to why my fan motor burnt out in less than two years, that’s another story. I’m definitely not happy about that. Never had that happen????
Response from GMC Air Conditioning Services, LLC:
Mr. Erskine, thank you for sharing and we are delighted to hear about your experience with our team. GMC Air Conditioning Services is always here to help and we appreciate your business!
Joanne - Miramar, FL
Great service !
Jessica - Miramar, FL
Service was incredible, the person doing the job knew exactly what was wrong from just looking at it and fixed it in no time. He even gave me recommendations that would come in handy someday. I give him 5 stars all the way ! Keep it up
In Hollywood, this customer arrived to perform the preventative maintenance for this facility with 20 air conditioners. Each system was tended to including equipment inspections, air filter changes and belt changes.
This facility in Hollywood was having an airflow issue as one of the back offices were very hot. After an investigation of the system, we discovered that a Mitsubishi mini split or another air drop needs to be added to that office.
For this commercial facility in Miramar, our technician replaced some of the water hoses apart of the line system of this AC. These lines bring water from the water pump to the air conditioner. After these were replaced, the system is back to cooling efficiently.
For this commercial customer in Miramar, we were called onsite for an AC leaking. After we ran a full diagnostic of the system, we discovered that the leak was not coming from the AC but it was coming from a sewage line over the women's bathroom.
For this commercial customer in Hollywood, our technician performed some much needed AC repair after discovering some issue during their preventative maintenance. This customer also inquired about an Indoor Air Quality product including things like air filters that help prevent the spread of viruses and bacteria.
For this residential customer in Miramar, we arrived at a system that isn’t cooling, after our technician ran a full diagnostic of the system he discovered that there were some things needed to get this YORK system back up and running. This includes a new compressor, contactor and capacitor. This customer has a 10 year parts and labor warranty, making this service visit at no cost to the customer.
We arrived to a system not cooling, after our technician is onsite we discovered that there was an issue with the compressor. Once that AC repair was performed the system is back to cooling.
We arrived to this commercial customer in Miramar to install a low profile condensate pump. This AC repair was discovered during our scheduled maintenance on the systems in this facility. This was a preventative measure to avoid an AC breakdown.
For this commercial customer, we arrived to correct an AC leaking water from the ceiling. After our technician ran a full diagnostic of this system in Miramar to find that the condensate pump was not secured and it fell from the wall. After we fixed the pump and the drain line, the system is back to functioning. We recommend replacing it with a low profile pump to allow more space between the pump and the ceiling tile.
For this commercial customer, we returned to do some preventative maintenance AC service including a deep cleaning of the system via an acid wash.
We arrived to this commercial facility in Hollywood to finish the preventative maintenance tailored for their system's needs. While onsite we discovered that one of the systems was in need of some ac repair. A quote was sent to the customer and the needed repairs we performed after customer approval.
During this residential maintenance, we ensure that all functions of the systems are working properly and there are no issues that need to be corrected. This precision tune-up is the type of scheduled maintenance needed to prevent breakdowns and costly repairs in the future.
As a Service Partner Plan member, this customer receives two scheduled maintenance a year to keep the system running properly. These are also a preventative measure to ensure the system is prepared for the summer, as well as prevents costly breakdowns and repairs in the future.
Heat pump / AC UNIT iEvaporator and compressor was found with heavy ice buildup
This unit was not cooling, after an inspection of the system the condenser fan motor was faulty. We replaced this motor which is an essential part of cooling the condenser coil. The condenser fan motor powers the fan that blows air across the condenser coil, where it cools the refrigerant from a hot gas into a liquid.
Preventive maintenance complete with unit checked for proper operation.
Service maintenance for York package unit
Repair leak on carrier split Air conditioning system unit pressure test and evacuated system charge up the system and checking operation
Service carrier Air Conditioning, split system and found leak
Unit working not cooling