GMC helps Davie, FL find 100% satisfaction with their air conditioning.
Read our Davie, FL air conditioning reviews to see our high ratings on our repair, replacement and tuneup services.
for Davie, FL
Our Reviews by City
Great speedy service
Matthew - Davie, FL
Response from GMC Air Conditioning Services, LLC:
Mr. Parke, first of all thank you for choosing GMC to install a brand new system for you. We know how big of a commitment it is and we appreciate you trusting our comfort consultant and installation team for this! We appreciate your business and the great review!
Shelia - Davie, FL
Response from GMC Air Conditioning Services, LLC:
Thank you for sharing your experience and we appreciate your business!
Dawn - Davie, FL
This customer is part of our service partner plan, which ensures her warranty is valid and to extend the life of her equipment.
In Davie, this customer was having some issues with their air conditioner cooling properly. While onsite, our technician found some much needed AC repair that was also covered under her warranty. This customer was back up and cooling in no time.
For this customer in Davie, we arrived to an air conditioner not cooling properly. The AC repair needed was minor and could have been preventated with regualr air conditioning maintnance.
For this residence in Davie, this customer was in need of some AC repair after we discovered a faulty part during our preventative maintenance. This customer has a 5 year parts and labor warranty which made this service call at not cost to the customer.
For this home in Davie, we returned to install a REME HALO indoor air quality product that ensures the highest air quality by using a UV to remove bacteria, viruses and other pollutants in the air. Installing a UV Light helps keep your home's air clean and preserve your family's health.
For this commercial customer in Davie, our technician returned to complete some AC repair that was approved by the customer and discovered during our preventative maintenance visit
Arrived to perform preventative maintenance on both AC systems at their home Davie. On site, we Cleared the drain lines, cleared the drain pans, added gel tabs, and changed the filter that the customer provided. We also sterilized the system with self rinsing chemicals. Once maintenance was complete checked systems for proper operation.
We arrived at this commercial facility to address two ac systems that were not cooling properly. After our technician arrived to the scene and performed a full diagnostic to discover what type of AC repair is needed in Davie. A lizard has crawled into the system and shorted some of the main electrical components.
This resident customer in Davie, the system was short cycling. After arriving on the scene and running a full diagnostic to ensure we have fount he problem, we discovered that the ac repair needed was adjusting some of the system pressures. after these adjustments, the system is cooling properly without any issues.
This customer called about needing her ac repaired due to it making an hiccuping noise with some trouble taking in air. After our technician was on the scene, he discovered that the motor was on the verge of breaking while causing the system to hiccup. The blower was also very dirty and contributed to the problem.
This residential customer in Davie noted that his system was leaking water, we advised him to shut off the system until our tech can get out there. Once the technician was on the scene we were able to clear the drain line which has the system back to working in top shape.
During this residential call in Davie, the customer reported that the system was freezing and leaking water. After review, we discovered there were multiple issues including an extremely dirty blower wheel causing improper airflow, the liquid filter was rusted out, and the condenser coil was in poor shape. Instead of suggesting repairs on this 23 year old system, we advised to replace it with a new, energy efficiency system. Our comfort consultant went out to this customer to suggest the best options for her home.
Since the unit was not cooling, we inspected the power source and concluded that the contactor needed to be replaced which allowed power to follow undisrupted through the unit. The condenser coil was not being cooled so we also replaced the condenser fan motor which restored the fan that blows air across the condenser coil, where it cools the refrigerant from a hot gas into a liquid.
During this tune-up, all safety controls and operating pressures were checked and lubrication was added to all moving parts. The system’s airflow was tested and the power levels were checked to make sure the unit wasn’t using excessive power use and optimal efficiency.
The unit was serviced as part of our annual air conditioning maintenance service plan where we performed a precision tune-up to ensure proper functionality of key components like the evaporator and condenser coil and cabinet, blower, airflow and refrigerant. The air filter was replaced and the drain pan was cleaned and algaecide was added.
Working on a Rheem Air Conditioning unit in Davie, Florida. Customer wanted to have better indoor air quality and a Reme Halo UV light was recommended. Installed UV light and checked for proper operation. UV light is now working and indoor air quality will improve due to Reme Halo.
Preventive maintenance complete with unit checked for proper operation.
Preventive maintenance performed inspect ahu blower motor drain lines deltaT20 inspect condenser coil pressure reading normal suction line 120 liquid line 320 sh12 sc 9 system running properly