GMC Air Conditioning is proud that Miami, FL residents and businesses relay on us for air conditioning repair, replacement or tuneup service.
We love our Miami, FL customer feedback on our air conditioning services.
See what your neighbors are saying about our services below!
for Miami, FL
Our Reviews by City
Diana - Miami, FL
Betty - Miami, FL
In Miami, there was some extensive AC repair needed for this commercial customer. This YORK system was in need of a new condenser coil, once this AC repair was performed this system was back up and cooling.
For this commercial facility in Miami, we performed the much needed AC repair while onsite for this preventative maintenance.
We were called out to Miami Gardens to address one of this facility's systems was not cooling properly. Our technician discovered that the AC repair needed included a fan motor and blade replacement.
We arrived in Miami to do the preventative AC maintenance created by our service manager to address the needs of their specific fleet.
In Miami, this commercial facility was due for their preventative maintenance. This air conditioning maintenance is important to insure peak performance especially on system that are used often and for long periods of time.
We arrived to this commercial facility to perform the preventative maintenance for this fleet of YORK systems. Since these systems are in constant use, it is extremely important to stay up to date on maintenance to avoid sudden breakdowns.
In Miami Gardens, this commercial facility was having some issues with their YORK system cooling. Our technician arrived to correct this breakdown and had their system up and running in no time!
For this commercial facility in Miami, we arrived to address an issue of an AC not cooling. After a full check of the system it was discovered that it was a thermostat issue. Once the thermostat was adjusted, the system was back to cooling.
For this commercial customer in Miami, we returned to perform AC repair that was discovered during our preventative maintenance visit.
For this residence in North Miami, we arrived to perform a precision tune up to make sure this system is running efficiently and to catch any needed AC repair before a potential breakdown head of the summer season.
For this commercial customer in Miami, we arrived to replace condenser fan motor and blade. When removing the old motor, we found the plate that secures the motor to the fan guard welds had failed. After repair, this system was back to running at peak performance.
We arrived to this commercial customer in Miami to a system AC not cooling. We arrived onsite to the AC's drain needing repair. The pump also needs to be replaced to get this YORK system up and running.
We arrived at this commercial facility to perform some much needed AC services and AC repairs including an evaporator coil cleaning and some duct repair.
Our technician arrived to this commercial facility in Miami Gardens to one of their suites’ AC not cooling, after a full diagnostic we performed we discovered that the batteries needed to be changed in the thermostat. The system still was not pumping the correct air flow to the suite so we checked the ducts and found that the main supply was being disrupted. Once approved, our technician performed the needed duct repair and everything as cooling normally.
We arrived to perform some much needed ac services on the system's at this commercial customer in Miami. Ac repair and ac services needed include: coil cleanings and duct work repair.
We replaced their old system with a brand new energy efficiency system. Now this customer will have better indoor air quality and efficiency.
We arrived at one of our commercial customer’s facility to help get one of their systems up and running. Once arriving on the scene, we began the ac repair. We found the system in bad shape due to lack of maintenance. We did the necessary repairs to get this system up and running. We will need to return to complete a full coil cleaning to ensure proper airflow through the unit.
This commercial customer in Miami Gardens called for ac repair on a system that was not cooling. We discovered that this system has never had regular maintenance or service. Firstly, the system is very old with a condensing unit from 2007 and a air handler from 1985. The system is in bad shape due to age including rust and damage to multiple key components. Due to the condition, our technician recommended against ac repair and offered a quote to replace instead.
We returned to this commercial customer’s facility to continue the maintenance on their extensive system. After performing a precision tune up along with changing the filters and clearing the drain lines, we discovered that the only service needed was a blower wheel cleaning in room 313.
We visited one of this commercial customer’s multiple facilities throughout South Florida for a system not cooling, after a full diagnosis of the problem we discovered that the condenser fan motor, blade and capacitor were faulty and needed replacement. After the new parts were installed the system has returned to cooling properly.
Performed preventative maintenance on a York AC system. During maintenance, we made sure to perform sterilization of Air handler. Once the system was sterilized, we ensured the unit was operating properly by performing a full system inspection. At this time the unit is working and cooling properly.
Preventive maintenance with unit checked for proper operation.