GMC has worked to be a leading air conditioning provider in West Palm Beach, FL for over 30 years.
Our efforts in West Palm Beach, FL have paid off immensely with rewarding relationships. We love when our customers take the time to tell us about what they receive from our services. Read all about it in our reviews below!
for West Palm Beach, FL
Our Reviews by City
Philip - West Palm Beach, FL
Efficient courteous and clean
Response from GMC Air Conditioning Services, LLC:
Mr. Shapiro, we are delighted to have you apart of the GMC team. Thank you for taking the time to leave your feedback. Thank you for your business and take you for the 5-stars!
GMC great service
Mayda - West Palm Beach, FL
GMC responded to my issue immediately with a knowledgeable, professional, courteous service technician.
In West Palm Beach, we arrived to install a brand new YORK system in a classroom. This new system has an extended warranty which ensures the cost of parts is covered in 10 years.
For this residence in West Palm Beach, we arrived to perform the preventative maintenance to help keep this customer' YORK system running at peak efficiency and to avoid sudden breakdowns.
We arrived in West Palm Beach to a customer having issues with their AC cooling at all. Our technician arrived to to address this AC breakdown and found that the system was down due to lack of AC maintenance.
Customer with water source heatpump condensation problem. Cleared drain line and adjusted pan for more positive drainage.
For this commercial facility in West Palm Beach, we arrived to finish some much needed AC repair for this Carrier system.
This commercial facility, they had who systems down that needed to be addressed. Our technician preformed a full diagnostic on both systems to figure out the issue. Once discovered, our technician preformed the much needed AC repair to get their systems back up and running.
This residential customer in West Palm Beach was having trouble with their older thermostat and Air conditioning. Our technician arrived and realize that there was going to be some extensive and costly AC repair, so our technician recommended AC repair
For this commercial customer in West Palm Beach, we arrived to a system not keeping their facility cool in the late afternoons. After our technician ran a full diagnostic of the system we discovered that the thermostat needed to be reprogrammed but there is a leak in the system. For now the system is cooling but we will need to return to address the larger issue.
We arrived to this commercial customer in West Palm Beach where their system was not bringing the room down to temperature. After running a review of the entire system, the thermostat needed to be reprogrammed. The drain line was also clogged which was causing a cooling disruption.
After a power surge over the weekend, our technician arrived to make sure the systems on site were still cooling properly. After a full inspection of the fleet, everything was fine and good to go.
We arrived to this commercial customer in West Palm Beach to complete the scheduled maintenance on their fleet of systems at this facility. Each system had their belts and filter changed, their operations checked and their drain lines and pans cleared.
For this commercial facility in West Palm Beach, our technician arrived to an AC not cooling properly. After we ran full diagnostic of the system, we discovered a wiring and electrical issue. Our technician was able to correct the problem onsite with the tools on his truck and get this system up and running again.
We arrived at this commercial facility to work on an AC making loud noise. Once our technician was onsite, he reviewed all key components and checked the electrical and safety features for proper functionality. After review, our technician This AC is supplying air to the IT room which can be very hot and needs cooling to function. There was extensive repair on this older system needed, and replacement is highly recommended. Our technician got the system running for the time being as the customer makes a decision on how to move forward.
We returned to complete the schedule maintenance for this extensive facility with a fleet of systems that need tending to.
For this commercial customer, we arrived to perform preventative maintenance on their fleet of AC systems. At each location, our technician reviewed the entire system for faulty parts or potential breakdown hazards, changed the filters, cleared the drain line and gave a report of findings for each system to the customer.
During this service call in West Palm Beach, this commercial customer needed us to install a new and important piece to their HVAC system. We furnish and install manual adjustable dampers to supply drops in career services. This will allow less air in that area and more into the front entrance hallway.
This residence in West Palm Beach was having some issues with their vents sweating. Our technician arrived to discover that some of the airflow was being disrupted causing the water issue. After opening up the air grills and switch up the power on the blower wheel, the system is back to flowing through the home properly.
We performed a precision tune up for this customer in West Palm Beach. This is helpful to prevent AC breakdown and extensive AC repair.
This commercial customer in West Palm Beach had a system not cooling properly. After careful review and diagnosis of the system we discovered that the system needed the capacitor and belts needed replacement. Once these repairs were completed the system is now running in tip top shape.
We received a call from one of our commercial customers about a system not cooling. Once we arrived on the scene, we determined that the system failure was due to a power surge during the most recent storm. After resetting the system, it was back to functioning properly.
For this commercial customer, they had two of their rooftop systems acting up. On the first system, it was not running due to a burnt out contactor which was causing the system over work. We replaced the faulty contactors and the system is running and cooling properly. On the second system, we found it running with multiple issues, two contactors needing replacement as well as the condenser fan and blade which was running backwards and causing an overheating in some of the electrical equipment.
During this commercial call in West Palm Beach, the customer advised that their Career Services Office was warmer than usual. Once we reviewed the system we discovered that the thermostat scheduling was incorrect. After updating the time and temperatures, the system was functioning properly and back to a normal cooling schedule.
Preventive maintenance with unit checked for proper operation.