GMC helps Hialeah, FL find 100% satisfaction with their air conditioning.
Read our Hialeah, FL air conditioning reviews to see our high ratings on our repair, replacement and tuneup services.
for Hialeah, FL
Our Reviews by City
Fantastic service, great price , and very professional!
Michael - Hialeah, FL
It has been a great experience having GMC replace all of my duct work. They brought everything up to code and the finished product is perfect!!! Very happy!
We arrived to this facility to address a system in the roof leaking. We meet roofers onsite to see if this was a plumbing issue or a HVAC issue.
We arrived to this facility to complete some much needed AC repair approved by the customer.
In Hialeah, we arrived to this commercial facility to address a water leak in the bathroom. While onsite, our technician discovered that some of the equipment was not insulated correctly, once fixed the system was no longer leaking.
Onsite in Hialeah, our technician arrived to an AC leaking water. Due to lack of maintenance, this system had a clogged drain line.
We arrived onsite at this commercial facility to preform much needed AC repair that has been approved by the customer. These AC repairs were discovered during our preventative maintenance for this commercial customer.
We arrived to this commercial facility in Hialeah for our routine maintenance created to fit their system's needs. All filters were changed and all the drain line were cleared as part of this routine maintenance.
This commercial customer had a system that was not cooling properly. Our technician went out to diagnose the issue return the system to peak performance and optimal efficiency.
Preventive maintenance complete with unit checked for proper operation.
Working at Florida career college in Hialeah one of our many valued commercial customers. Customer has an office that is very warm. Found that room was warm due to supply grill for the room being a blank supply meaning it was not connected to the unit. Also found that actual supply drop that was connected to unit was above drop ceiling. Removed blank supply and put actual supply drop back in. Unit is now providing proper air flow to the office and we have a very happy customer.